Metric and Decimal Drill Bits
Home Tags Metric and Decimal Drill Bits
Tag: Metric and Decimal Drill Bits
Dear Mr. Electrician: What are the standard electrician's screw drill and tap sizes for electrical switch and outlet boxes? Answer: 6/32, 8/32, 10/32 are the most commonly used electrician's screw drill and tap sizes in electrical boxes installed in the USA. NOTE: Some text links below go to applicable products on Amazon. As an Amazon Associate I earn from qualifying purchases. 6/32 screws are used for mounting a wall switch or an electrical receptacle outlet to the electrical box in the wall and also for the finished wall plate. #6 is the screw size and 32 is the number of threads per inch. 8/32 is used to hold the covers on certain electrical boxes and for light fixture support. 10/32 screws tend to be used for grounding metal outlet, junction, and switch boxes. I have noticed that some light fixtures made in other countries have screws included with them that look like 8/32, but are a little tight when screwed into a standard ceiling electrical box in the USA. I found out that they are not true 8/32 screws, but are actually a metric equivalent made to accommodate the American lighting fixture market. The hardware shipped with such light fixtures also use these odd screws, but I have used my Klein Tools 6-in-1 tapping tool, if needed, to make them true 8/32 without any problem. Some ceiling fan boxes use 10/24 screws for the fan mount. 10/24 screws were also used for the cable clamps in very old black enameled switch and outlet boxes. For grounding it is important to use fine threaded machine screws such as 10/32 to attach a ground wire to a metal electrical box or a grounding lug to a metal enclosure. The reason is because laboratory testing has determined that a minimum of two and a third screw threads must be in contact with the metal that is being grounded in order for it to be an effective ground connection. That is why sheet metal screws and wood screws cannot be used for grounding connections. Below is a table of drill and tap sizes, some of which are used during the course of installing electrical wiring. I have also included the decimal equivalent. Many of the plastic switch and outlet box types do not have threaded holes. The screws thread into a precisely sized hole in the plastic box, no tapping is necessary. I always have my 6-in-1 Klein tapping tool in my tool bag. It has the most common drill and tap sizes for electricians and comes in handy. If the threads are stripped on a metal outlet or junction box, you can sometimes re-tap the hole to the same size or the next bigger screw size. If paint or joint compound gets in the screw holes, the 6-in-1 tapping tool is quick to clean them out. Replacement taps are available for the Klein 6-in-1 tap handle however I have found that the best place to buy them in terms of low price and availability is at an electrical supply company that sells Klein...