The building was built in the 1980’s. With proper maintenance there would have been no need to replace this 4 gang electrical meter socket box.
The gas piping is very close to the electric utility and would probably not be allowed today. The gas pipes look as though they could use some maintenance as well. On the left side between the bush and the window is the new meter base in a box and covered with a plastic sheet.
The new board was installed using primed deck screws. I also caulked the top and sides of the opening before putting the new board in place.
We had to be careful with the length of screw that we used as some of the tenant feeder wires pass through the vertical wood studs.
A two inch (trade size) hole was made in the bottom with a knockout punch to accommodate the existing 2″ PVC conduit coming out of the ground. 3″x 2″ Reducing washers were used to protect the concentric knockouts from breaking loose. This photo is from a different meter base replacement in the same neighborhood.
Temporary power for our tools is usually derived from another nearby electric meter base circuit breaker or from a willing homeowner. A portable generator could also be used for temporary power. Some of my power tools were battery powered so I had extra fully charged batteries on hand.
A reducing washer is sitting on the PVC conduit connector ready for the new meter base. The #2 aluminum wires were too short to reach up to the new main circuit breakers. Short pieces of wire were added by using split bolt connectors rated for aluminum which were wrapped with rubber tape and then vinyl electrical tape. The above photo is from a different meter socket replacement in the same neighborhood.
Note the new intersytem bonding termination to the left of the PVC conduit. A five gang electric meter base was used to accommodate the existing tenant load wires. Four gang meter socket bases are only available as a vertical stack now.
When the power company returned to restore power from the transformer, a meter person also arrived and installed brand new electric meters. Stick-on numbers were added later on the black circuit breaker covers to indicate which breaker and meter were for each condominium.
To help preserve the new 4 gang electrical meter socket installation I caulked the top where it meets the building with clear outdoor gutter and flashing silicone caulk. I also caulked around the top hub covers. Those are the two areas I have found that water is likely to enter.
The 23/32″ CDX plywood backboard was primed and then painted all around a few days ahead of time. I always cut the board and have it primed and painted days before the replacement work so that we could focus on getting power restored as quickly as possible.
The meter person from the power company put the new seals and locks on after installing the new electric meters. I added some stick-on numbers to the black circuit breaker covers after this photo was taken.
I left a loop of #4 green grounding conductor wire above in case the other utility companies wanted to connect to that rather than the intersystem bonding termination. You can see that multiple clamps from TV and telephone utilities were attached to the old ground rod.
Because the ground rod was the only connection to earth I installed two new ground rods at least sixteen feet apart. I also kept the connection to the existing ground rod because other utilities were connected to it. I installed an intersystem bonding termination, but left it for the other utility company’s to make their connection to it.
I doubled the wire end over for better contact. I drove the ground rods and put the grounding conductor in the ground a few days before so that we could focus on getting power restored to the building as quickly as possible. I used a rotary hammer with a ground rod driver attachment to drive the ground rods.
I always laid down a cheap lightweight plastic tarp to keep the tools and materials from getting lost and from getting wet.
TOOLS TO REPLACE 4 GANG ELECTRIC METER SOCKET
Tools on hand for the electrical meter socket replacement included a hydraulic knockout punch set, hole saws, reciprocating saw, circular saw, oscillating multi-tool, cordless pistol drills, cordless angle drill, caulk gun, impact driver. Also needed was a socket set, ratchet, and torque wrench to tighten the electrical connections.
Allen wrenches were used in addition to lineman pliers, Knipex high leverage diagonal pliers, screw drivers, Channellock pliers, Half round files, knife, four foot ladder, and a work table.
Also used were a shovel, 4″ trench shovel, pick ax, pry bars, paint brushes, wire brushes, sandpaper, painter’s scraper to remove old caulk, extension cords, GFCI portable outlet box, goggles, gloves, and a hand truck. I had bolt cutters and a large crimper available if needed.
Looking at the rusting pattern inside shows that water was mostly entering from holes in the back rather then from the top cover. However I have also seen instances where the top cover was the culprit.
MATERIALS USED TO REPLACE 4 GANG ELECTRICAL METER SOCKET
Materials for this job included one 5 socket electric meter base – Siemens #SP4511RJB (I think this Part Number has Changed), four 2 pole 100 amp Siemens main circuit breakers (Type Q2100H), exterior wood primer, exterior wood paint, 23/32″ plywood, 2 ground rods, two ground rod clamps, #4 copper grounding wire, #2 aluminum THWN, aluminum rated split bolt connectors, rubber tape, black vinyl electrical tape, aluminum anti-oxidant compound, four 1 1/4″ chase nipples with locknuts and plastic bushings, one 3/4″ chase nipple with locknut and bushing for the ground wire entering the rear, 2″ and 2 1/2″ primed deck screws.
In addition 1 1/2″, 2″, and 2 1/2″ x #12 sheet metal screws, GE silicone II Gutter and Flashing caulk, intersystem bonding termination, small cable straps for ground wire, a button Romex connector for the ground wire, green electrical tape, white electrical tape, fender washers, stick-on numbers, foam backer rod, cheap plastic tarp for grass cover, pieces of wall insulation to stuff into the wall, and duct seal to fill the chase nipples to reduce the amount of cold air going into the wall. I also had a can of Rust-OLeum industrial gray spray paint on hand for touch-up.
Click for information about Siemens 4 gang electrical meter sockets.
My post on concentric knockout removal may be useful to you.